Figure shows the comparison between the original and current airfoil designs. The old airfoils form a channel in which steam flow accelerates and turns to exit with maximum steam velocity resulting in high secondary losses.
Current airfoils form a channel in which steam flow turns first with low steam velocity and then accelerates. Low steam velocity forms a thin boundary layer resulting in low secondary losses. The current airfoil design has two other advantageous features; it is much stronger than the original design and it has improved inlet edge geometry. The latter allows for steam flow at a wider range of angles without significant separation. Using the new airfoil design yields an increase in stage efficiency of 0.5-1.0%.
(Tutorial on steam turbine airfoils will continue in subsequent weeks)
Turbomachinery Blog features postings from experts in all areas of turbomachinery, such as: gas turbines, machine diagnostics, materials, repairs, and aftermarket parts, and encourages users to participate, with reader engagement and interaction as its primary purpose.
|There are no products|